Rated 4.6 out of 5 by 14
Rated 5.0 out of 5.0 by MRGoose Solid, Affordable, and Easy
This kit was a perfect fit for my 15 year old Cutler-Hammer 150amp load center and at a very reasonable price compared to others. I did not have pre-marked holes, but I followed the provided instructions for drilling them out and everything lined up.It feels solid and comes with all of the extra pieces needed to meet code (stickers and hold down screw).
One thing to note: If you intend to use this with a 30 amp breaker you will have difficulty finding one with the hold down screw hole. Eaton does make one, but it is not carried in store. It is part# BR230B, not BR230). Using a higher amp breaker as template - I was able carefully drill the hole in my regular BR 30amp breaker, but I wouldn't recommend that for everyone.
September 6, 2016
Rated 5.0 out of 5.0 by Kathy Perfect order
The generator interlock kit arrived in two days, had everything in the kit that was advertised, and best of all it was easy to install and my generator was up in running in less than thirty minutes. No problems whatsoever! Thank you Home Depot!
August 16, 2016
Rated 5.0 out of 5.0 by electrician Great Item
Easy to install and a life saver at that. Keeps generator from back feeding thru the utility service.
July 6, 2016
Rated 5.0 out of 5.0 by jenkins great product for the BR series panels
We are a Electrical Contractor and have a hard time finding this interlock kit at our supply houses, the great thing about this product is there is no doubt on the UL listing with other after market kits out there this is always a concern.
March 22, 2016
Rated 5.0 out of 5.0 by John Well made safety item
Generator interlock kit is very well made and works as intended. Installation instructions must be read and followed carefully. Kit is expensive but necessary for safety and code compliance.
March 22, 2016
Rated 3.0 out of 5.0 by smartyshorts good
Expensive and had to adapt a bit. Drill in new spots
January 19, 2016
Rated 4.0 out of 5.0 by Chuck Great product
Great product from Eaton, worked well. Could use a little better installation instructions!
December 15, 2015
Rated 5.0 out of 5.0 by ac Good for Eaton/Cutler Hammer 200 Amp load center with top center main breaker
I initially hesitated at the price for a simple metal plate, but grew frustrated shopping for a transfer switch so I gave in and bought this. I'm glad I did. You get a quality product, and the flexibility to access your entire panel and choose the circuits you want to power at any given time (subject to your generator's capacity).
The 2 assembled plates are made of a heavy gauge steel, powdercoated, and do slide very smoothly. The kit includes the breaker holddown plastic block and long screw, which are available as a separate kit that you do not need to buy (BRHDK125). The dedicated holddown device for the backfed circuit breaker is required by code. The kit also includes stickers that contain the written warning notices required by code for the installed backfeed system (interlock plate, backfeeding breaker, backup generator).
November 6, 2015