A: No it is not. GE breakers are only rated for GE panels. Cutler-Hammer breakers are compatible with Challenger panels.
A: Yes BUT very important was breaker is powering and wire size cause if won’t trip because AMP on breaker to high the wire going to what breaker shuts off could catch fire
A: Yes, it should be a direct replacement. The breaker you asked about is a newer model.
A: No, it does not. RT-692 is GE Type THHQB, Bolt On Mounting, 22kAIC RT-693 is GE Type THQL, Plug In Mounting, 10kAIC Part number decoding: T = GE product type H = 10kAIC HH = 22kAIC [Current interrupting capacity] Q = Q Line family B = Bolt On L = Plug In
|Name||Q-Line 50 Amp 1 in. Single Pole Circuit Breaker||70 Amp 1-Pole 10 kA Type QP Circuit Breaker||40 Amp Single Pole Bolt-On Breaker||35 Amp Single Pole Bolt-On Breaker|
|Interruption Type||Standard Trip||Standard Trip||Standard Trip||Standard Trip|
|Breaker Type||Single Pole||Single Pole||Single Pole||Single Pole|
|Mounting Type||Plug-On||Plug-On||Bolt On||Bolt On|
|Power Distribution Features||No Additional Features||No Additional Features||No Additional Features||No Additional Features|
|Electrical Product Type||Breaker||Breaker||Breaker||Breaker|
|View Product||View Product||View Product||View Product|