No, it is just 3 pieces of metal (one of which is a template that gets used and then tossed) and a few screws - what you're paying for is the convenience of being able to do a generator hook-up that meets code without needing an external transfer switch.
Hello Mark, No, this is a Homeline interlock kit compatible only with Homeline load centers. Based on the information you provided you have a QO load center. You need the part number QOCGK2C, is compatible for use with any Series G and S, NEMA Type 1 (indoor) and Series G and S1, NEMA Type 3R (outdoor), single phase, convertible QO main breaker load center that utilizes a QOM2 frame main circuit breaker (150 - 225 amp MAX.). Warm regards, Schneider Electric Customer Care
Hello, Yes. You can use the HOMCRBGK1C in the HOM2448M100PCVP load center. Regards.
Hello, HOMC30UC is the part number of the cover, we need the part number of the complete load center to answer your question but, here is a link to one of our FAQs called "What Generator Interlock Kit is available for use with Homeline Convertible Main Breaker Load Centers(or Convertible Main Lug Load Centers that get converted to MB with a QOM1 or QOM2 MB)?" : https://www.se.com/us/en/faqs/index?page=content&id=FA238193&actp=search&viewlocale=en_US This FAQ explains how to select an interlock for your load center based on its features. You can contact us anytime using our chat live https://www.se.com/us/en/work/support/customer-care/contact-schneider-electric.jsp where an agent will be able to give you further assistance on this matter. Warm regards. Schneider Electric Customer Care
Hello Ricky, There is not enough information to determine if your load center can use the HOMCRBGK1C. The catalog number in the photo is just the catalog number of the cover. In order to determine the correct interlock kit you need to provide the catalog number of the load center. I invite you to check our Frequently Asked Questions and use the FA274608 article. This article will help you to find the catalog number of your load center. Regards.
Hello Enoch, The catalog number for a generator interlock kit for a HOM2448L125PGC is HOMCRBGK1C. However, you need to field install a main breaker because the HOM2448L125PGC is a Main Lug convertible main load center. You have to install a QOM1 style main breaker. Regards.
Thank you for the fast reply! I will look into transfer switch boxes.
Probably not, this interlock is designed to work with Square D products.
NO NO NO, Please hire a licensed electrician. Your panel is a LUG panel and does not have a main breaker
Hello, The selection of the correct Generator Interlock Kit is dependent upon the Series Number of the Homeline load center. Any other series not listed below does not have a generator interlock kit available. The HOMCGK2C is compatible with any Series S, NEMA Type 1 (indoor); and Series S1, NEMA Type 3R (outdoor), convertible main, main breaker HOMELINE load center that utilizes a QOM2 frame main circuit breaker (150 - 225 ampere). It interlocks the QOM2 2-pole main circuit breaker with a back-fed HOM 2-pole (15-125 ampere) branch circuit breaker. A retaining means is also provided for the back-fed HOM branch breaker. NOTE: Convertible Main Lug Only load centers, that meets the description provided above, could also be used by converting the load center to a Main Breaker device. Regards, Customer Care Center