Store SKU #
A: Hello, unfortunately the lever is not a replaceable part. Regards, Schneider Electric Customer Care
A: Hello Jesse, This unit includes the M1 form for a maintained manual cut-out lever. The switch will stay off when lever is manually set in the off position. The lever will then need to be reset manually to start the operation again. Depending on your application you can use this unit as a replacement for 9013FSG2. You will also have to verify the pressure settings of your older unit. Regards, Schneider Electric Customer Care
A: Hello Duff, This pressure switch is Single Phase AC rated 1 1/2 HP at 115V, 2 HP at 230V and 3-Phase rated 2 HP at 115V, 3 HP at 230V, and 1 HP at 460/575V. Regards, Schneider Electric Customer Care
A: It has 2 positions, down is on voltage to the pump and up is off ..