In Canada, this 2 pole double throw switch is￼ expressly intended￼ for "NEUTRAL FLOATING" generators ONLY. And it's 100/60 amp rating make it￼ suitable for￼￼ whole-home transfer switching with 100 amp service￼. "NEUTRAL BONDED TO FRAME" generators require a 3 pole double-throw transfer switch. 3 pole double throw transfer switches "maybe" configurable to either type of generator, and can cost 2 to 3 times more $$$.￼ Retail regulations require this info be illustrated on label near receptacles of the generator sold in Canada￼￼. This is a quality, cost effective transfer switch, but choose wisely when configuring with intended generator.￼ Recommended.