A: Yes, it is exactly 500ft. There will be enough for two pulls.
A: : Please check with your local electrical or building inspector for their judgement on this issue.
A: 6 AWG USE-2 can handle 30 Amps, however a length of 140' will have excessive voltage drop (5.25% for 120V appliances). To keep the voltage drop below the industry recommendation of 3%, you would need 3 AWG AL conductors or 4 AWG CU conductors. You can use our voltage drop calculator for these calculations: https://www.southwire.com/calculator-vdrop
A: We are happy to help! Please consult with our team at email@example.com for further assistance.
A: no, it's a single cable for direct burial. You'd have to buy the ground wire separately.
A: No, it does not include an un-insulated ground cable.
|Name||1000 ft. 6 Black Stranded AL USE-2 Cable||1000 ft. 1/1 Black Stranded AL USE Cable||500 ft. 4-4-4-6 Gray Stranded AL SER Cable||500 ft. 4/0 Black Stranded AL USE-2 Cable|
|Total Wire Length (ft.)||1000 ft||1000 ft||500 ft||500 ft|
|Max Amps||Not Specified||Not Specified||Not Specified||205|
|Wire Cut Type||Pre-Cut Length||Pre-Cut Length||Pre-Cut Length||Pre-Cut Length|
|Features||Heat Resistant,Jacketed,Waterproof||Heat Resistant,Jacketed,Waterproof||Heat Resistant,Jacketed,Waterproof||Heat Resistant,Jacketed,Waterproof|
|Stranded or Solid||Stranded||Stranded||Stranded||Stranded|
|View Product||View Product||View Product||View Product|