A: No, this is only for GE panel You would need an Eaton CH breaker
A: This breaker is not UL approved for use in other manufacturer's brands except GE. Thanks for the question.
A: GE breakers are not listed for use in Cutler Hammer load centers or panels.
A: GE circuit breakers are only designed to be used in GE circuit breaker panels
A: Only the new style, but it is not allowed by code. Breakers should only be installed in manufacturer specific panels.
A: No, by Law and The National Electric Code, this breaker is only rated for GE panels.
A: Breaker will fit, but it's not UL-approved. Better to use Eaton BR type breaker.
|Name||Q-Line 100 Amp 2 in. Double-Pole Circuit Breaker||100-Space Amp Double-Pole Type QP Circuit Breaker||Q-Line 80 Amp 2 in. 2-Pole Circuit Breaker||New VPKUBIF Thick 60 Amp 2 in. 2-Pole Federal Pacific Stab-Lok Type NA Replacement Circuit Breaker|
|Breaker Type||Double Pole||Double Pole||Double Pole||Double Pole|
|Interruption Type||Standard Trip||Standard Trip||Standard Trip||Standard Trip|
|Power Distribution Features||No Additional Features||No Additional Features||No Additional Features||No Additional Features|
|Electrical Product Type||Breaker||Breaker||Breaker||Breaker|
|THD SO SKU||516939|
|View Product||View Product||View Product||View Product|