Yes, it will handle 2-100 breakers. No, they don't have to be in any particular place in the panel. Jim
Not advising to use this panel as a sub panel since neutral and ground are bonding. Unless you install ground strip seperately.
Yes. You can use it as a subpanel. Just don't install the green bonding screw and install a PK23GTA ground bar for your ground connections. Regards, Schneider Electric Customer Care.
I would have no idea without going to that page and setting "My Store" at the top of the page to a store in Bakersfield that you normally use and then checking inventory at that store. If they have no inventory then you check the nearby stores. All of this you do yourself. If that doesn't work for you, call the store you normally use and talk to the electrical dept. associate on duty and ask him to check where they may have inventory.
Hello, Yes. You can install a double pole, 30A, HOM breaker. Verify with your local electrician what HOM breaker will you require for your application. Regards, Schneider Electric Customer Care.
Hello Dave, This is a Main Breaker load center. Regards, Schneider Electric Customer Care.
Contract a License Electrician to install electrical products. Thank you!
Hello, As our world continues to experience unprecedented challenges due to the COVID-19 pandemic, we’d like to share an update on our efforts to service our customers. Due to COVID-19, we experienced an unavoidable impact at one plant producing the following products: • QO/QOB and Homeline, two and three pole breakers • QO/QOB and Homeline, Arc Fault Breakers, Dual Function and Ground Fault Breakers • QOU, one, two, and three pole breakers We are working hard to improve and increase production levels as quickly as possible. We continue to monitor this pandemic and adjust to market demand swings. We remain committed to serving your needs and we greatly appreciate your patience, support, and partnership. To supplement our production and avoid future disruptions, we have added manufacturing capacity in three existing plants in North America. This increases production output, provides duplicate production locations and accelerates recovery. This action is critical in driving the incremental 30% capacity above pre-COVID production levels accelerating our recovery time. We continue to monitor this pandemic and adjust to market demand swings. Warm regards, Schneider Electric Customer Care
This can sometimes be done by a skilled electrician, but generally is not recommended if there are any other options available.
Hello Hunter, You can replace the cover HOMC42UC. Or, you can also replace the Indoor Cover Hinge - 4028356450K (Kit contains parts to repair one hinge) and the Door Latch Kit - 4020284450K. Just verify that your model is series S04. Regards.