A: Please reach out to our expects at CableTechSupport@southwire.com
A: Per NEC Table 310.15(B)(16), a 2 AWG copper USE-2/RHH/RHW-2 conductor is rated for 115 Amps (at 75C). It is large enough for 100 Amps however if using the full 100 Amp load (which is unlikely), the voltage drop will be a little bit higher (3.24%) than recommended (3%). The above advice is based upon the current edition of the National Electric Code (NEC). Free access to the latest version of the NEC is available online at www.nfpa.org/freeaccess. The NEC and local building codes regulate the types of wire and cable that can be used in specific electrical applications, as well as the manner of installation. Check your local building codes before you start any wiring and cable electrical project and be sure to obtain required permits. When your work is complete, always have it inspected for compliance with local codes to ensure that it has been safely installed.
A: Please contact CableTechSupport@southwire.com for further assistance.
A: yes this wire is rated for up to 125 amps
|Name||1000 ft. 1/1 Black Stranded AL USE Cable||1,000 ft. 1/0 Black Stranded AL USE-2 Cable||500 ft. 2 Black Stranded CU USE-2 Cable||500 ft. 4/0-4/0-2/0 Black Stranded AL Sweetbriar URD Cable|
|Total Wire Length (ft.)||1000 ft||1000 ft||500 ft||500 ft|
|Max Amps||Not Specified||Not Specified||Not Specified||Not Specified|
|Wire Cut Type||Pre-Cut Length||Pre-Cut Length||Pre-Cut Length||Pre-Cut Length|
|Features||Heat Resistant,Jacketed,Waterproof||Heat Resistant,Jacketed,Waterproof||Heat Resistant,Jacketed,Waterproof||Heat Resistant,Jacketed,Waterproof|
|Stranded or Solid||Stranded||Stranded||Stranded||Stranded|
|View Product||View Product||View Product||View Product|