A: I have a full size Qi CFGI 50 amp (hot tub) and full size smaller amp units in mine. It’s also easy to install with expect amount of room
A: Hello Kyle, The surge arrestor for this load center is #QO2175SB. You can contact us anytime using our chat live https://www.se.com/us/en/work/support/customer-care/contact-schneider-electric.jsp where an agent will be able to give you further assistance on this matter. Warm regards. Schneider Electric Customer Care
A: Hello Danny, Yes, it is a plug on neutral. Regards, Schneider Electric Customer Care.
A: In order to answer your question, a few questions need to be answered by you. Is the "new" Square D QO 100 amp 6 space panel going to be used as the main service panel (the first panel wired from your electric meter or main service disconnecting means)? If the answer is "YES", then the ground wires can be attached to the Neutral bar as long as you have enough spaces to only install one wire under each connection point on the Neutral bar. If not, then you should add another Neutral bar or a ground bar kit to attach the ground wires. If the "new" Square D QO 100 amp 6 space panel is going to be used as a subpanel (getting its feed/power from the main service panel), then the answer to your question is "NO" as the neutral and ground wires should not be combined on the same termination point except at the Main Service Panel. Hopefully, this makes sense to you and if not I would highly recommend that you contact a licensed electrician for your installation.
A: Hello, For the grounds, you need to add a ground bar. The catalog number for the ground bar for a QO612L100RBCP is PK7GTA. Regards, Schneider Electric Customer Care.
A: There is no longer any such thing as two phase. The only thing that seems to be provided currently by power companies for normal usage is single phase or three phase electrical services. The Square D QO 100 amp 6-space 12-circuit outdoor main lug load center with cover is designed to be connected to a 120/240 Volt electrical service which would be supplied by 2 Hot wires and one Neutral wire with a ground also. This is called a single phase power hookup. A three phase hookup has 3 Hot wires and usually a Neutral wire with a ground wire also and cannot be installed in this panel as it only has two lugs for Hot wires to be attached to and the bus bar is not designed for three phase power. With the single phase, 120/240 hookup that this panel is designed for, you can get 120 volts by using a single pole breaker and a Neutral and 240 volts by using a double pole breaker by using two Hots (opposite phase) on a double pole breaker. Higher voltage can be provided for industrial usage but not installed in this panel as it is not designed for such. Usually the higher voltage would be three phase.
A: Hello, The QO612L100RBCP can be used for single phase, 3 wire applications only. Regards, Schneider Electric Customer Care.
|Brand||Square D||Square D||Square D||Square D|
|Name||Homeline 70 Amp 2-Space 4-Circuit Outdoor Main Lug Load Center(HOM24L70RBCP)||QO 70 Amp 2-Space 4-Circuit Outdoor Main Lug Load Center with Cover||QO 100 Amp 8-Space 16-Circuit Indoor Surface Mount Main Lug Load Center with Cover, Door||QO 100 Amp 8-Space 16-Circuit Indoor Flush Mount Main Lug Load Center with Cover, Door|
|Maximum Amperage (amps)||70||70||100||100|
|Number of Spaces||2||2||8||8|
|Mounting Type||Plug-On||Bolt On||Plug-On||Plug-On|
|Load Center Type||Main Lug||Main Lug||Main Lug||Main Lug|
|Number of Circuits||4||4||16||16|
|Load center width (in.)||4.88||4.88||8.88||8.88|
|Load center height (in.)||9.38||9.38||12.57||12.57|
|THD SO SKU||1000112061|
|View Product||View Product||View Product||View Product|